1. CASE STUDY- ALCHEMIST:
PROJECT : RECYCLING OF SEWAGE TREATMENT PLANT TREATED WATER
PRODUCT : 150 KLD WATER TO BE REUSED IN HVAC & FLUSHING
LOCATION: PANCHKULA, HARYANA
Hospital is located at Panchkula Sector 21; sewage generation is approx. 150 KLD (including Liquid biomedical waste).
For LBMW, ETP of 40 KLD is installed for disinfection and TSS removal, outlet of ETP will mix with sewage water in equalization tank for biological treatment.
- The wastewaters from the domestic utilities are collected in the collection Tank
- One 16 mm followed by one 6 mm manual screen shall be supplied at the inlet of equalization tank to remove the debris. The equalization tank should be equipped with diffusers for homogenizing the influent sewage.
- The equalized wastewater will be pumped through 2MM punched whole fine screen to the MBR System. This System is a packaged unit with common Bioreactor tank, Membrane tank and Dip tank. The Dip Tank is partition made in the Bioreactor tank for cleaning of the membrane modules. The permeate from the MBR system will be discharged in a treated water tank.
- From the treated water tank we have installed a softener unit for recycling.